Welcome to the Home Performance Forum - hosted by the Home Performance Coalition
Previously the RESNET BPI – Energy Audit and Home Performance LinkedIn Group
Welcome to the new Home Performance Forum.
It looks like you're new here. If you want to get involved, click one of these buttons!
Forum admin, posting rules & FAQs
LinkedIn Group Archives
Coffee Shop (BYOC)
Envelope & Building Science
Windows & doors
Insulation & air sealing
Moisture & vapor control
Framing & structural
Everything else (envelope & building science)
HVAC & Other Building Systems
Heating & cooling
Ventilation & IAQ
Domestic hot water
Lighting, appliances & other electrical loads
Energy monitoring & data logging
Onsite power, energy storage, net metering & smart grid
Water quality & conservation
Energy Audits & Ratings
Other score-based assessments
Diagnostic tools & testing protocols
Programs, Codes, Standards & Training
Asset rating programs (E*, HERS, PHIUS, LEED, HES, etc)
Incentive programs & public policy
Energy codes & standards
Training, certification & professional development
Home Performance Enterprise & Marketing
Sales, financing & other marketing topics
CRM, accounting & other business tools
Social media & website design
Announcements, Ads & Jobs
Trade shows & conferences
Training classes & programs
Webinars & other events
Products, services & promotional blogs
For sale & wanted ads
Job listings, job seekers & referrals
Geothermal with 80 gal tank
edited April 17
Anyone know how to model the water heater portion of a geothermal system? Not much experience with geothermal. Thanks for any help!
The equipment manufacture will have a modeling tool that includes desuperheater performance by temperature bins. For example, ClimateMaster's tool is called Geo Designer. Whether or not this is useful depends on what you're trying to accomplish. Are you doing life-cycle cost analysis or a HERS rating? Or something else?
Thanks, David! This is for a HERS rating. I can figure out the specs on the heating and cooling parts but not sure how to deal with the water heater portion.
edited April 19
Excellent question. I'm moving this discussion to the HERS ratings category.
First, it's important to specify whether you're talking about a desuperheater or a water-to-water heat pump. A desuperheater cannot supply 100% of DHW since it's a byproduct of the heating/cooling compression cycles, thus the setup typically involves a secondary storage tank on the input side of the primary water heater.
A water-to-water heat pump produces hot water directly and thus can be dedicated to DHW, or more likely, serve double-duty for hydronic spacing conditioning and DHW.
Note that the impact of a desuperheater on overall DHW efficiency is not covered in the RESNET standard. This means it's up to the software developer as to whether and how it's captured in the HERS rating.
Please clarify which type of system and which software you're using and I can provide further guidance.
Thanks, David! Yeah, it's a desuperheater and I'm using REM/Rate.
edited April 19
OK, then.You need to set up your primary water heater as you normally would, then open the equipment properties form for the geo heat pump. There should be a checkbox for 'desuperheater'. I don't have latest version of REM/Rate, so let me know if you don't find this option.
I just ran a quick test on my own home. With primary DWH set to electric and one of the standard geo heat pumps from the library, my HERS score was 63. When I select desuperheater option, it drops to 59. If your primary DHW is natural gas, I would expect a smaller drop, but I didn't test that.